Fire Systems of Michigan
Bay City, MI
easy to work with
Great Customer Service
hardworking and very polite and knowledgeable
always business with a smile
Bay City, MI
Great service. Unsure on price, have not received final invoice.
Grand Rapids, MI
Kitchen Suppression Inspection
Portable Extinguishers Inspection
Contacted Brian Briggs, he informed me that he would like us to remove the front door Mag lock and power supply and any wiring connected to fire alarm system. And dispose of parts. Front door mag lock system is no longer is use and must be removed, and disconnected. Removed front Door Mag Lock and power Supply and removed and disconnected all wiring connected to FACP. ***All Systems Normal and Reset ***
Replaced 2-Smoke Alarms that were EXPIRED. Tested and reset smoke Alarms ***All Systems Normal and Reset ***
Replaced Crawl space Duct Smoke and Re-Wired( Had to Run Wire for Power from FACP through crawl space to Duct Smoke Approx 15 ft) Also Installed New Remote Test station In Furnace Room (Existing Test switch is non Compatible with New Duct Smoke) Tested and Reset Duct smoke at Remote Test station and at Duct Smoke Unit) Alarm system trips properly and resets properly. Duct smoke is connected to zone 3 (Waterflow/Duct smoke). If Customer wants furnace shut down wired in (HVAC Tech will have to bring own wire to duct smoke and wire into on-board contacts). ***All Systems Normal and Reset ***
Call cell when you get there. 862-579-7184 TD 1.17.20 Ivy approved inspection @ 230p TD 1.6.20 Ivy approved and will be on site @ 230p (closed on Monday's--schedule on Monday) 12/30-Called to schedule NW 12/31/19 - Ivy said she will call back next week. Portable Extinguishers and Kitchen Suppression Inspection Annual Fire Extinguisher Inspection Semi-Annual Kitchen Suppression System Inspection PyroChem PCL-460/300 (3)500 links (4)360 links (15)Nozzles Deficiency: PCL-360 tank is out of hydro date.
Picked up (14) fire hoses for hydrostatic test
Alarm Systems Service Call
Upgraded kitchen suppression system to a pcl-460 Knight 2. Replaced all 11 nozzles to Knight 2. Reworked pipe above fryers and left side woks for proper protection.
TD 1.23.20 googled business, called and spoke to Sonja she approved the inspection @ 10a TD 1.15.20 VM full - no msg TD 1.7.20 VM full - no msg Kitchen Suppression Inspection
Providing faster, smarter, and more efficient fire protectionLog in