for Shelby Township, MI
Karen - Shelby Township, MI 48316
Very polite & friendly. Communication was good!
George Smith Excellent Pro
Pete - Shelby Township, MI 48315
George is a pro!
Awesome professional service
Michael - Shelby Township, MI 48315
Fire pros always does a thorough job
Andre - Shelby Township, MI 48317
great professional and friendly
5/9/23 Confirmed by Karen for 5/9/23/ Please call Kate upon arrival to put system into test 586-996-3647 DH 2/17/23 Customer doesn't want the inspection until April 2023 DH 1/11/23MV Emailed customer regarding inspection date 1/18, She does not need this inspection done as of right now' Sprinkler Inspection Annual Fire Sprinkler Inspection (1 Dry System) Full Flood Due: 2024 Deficiency: 5 year internal pipe inspection due. 2 new 4” victaulic couplings 2 new 2” victaulic couplings. Entire ceiling is drywall, 2 access doors to reach piping. Need 6” ladder Deficiency: 5 year internal check valve inspection due for fdc valve and alarm check valve. Need 2 new 4” victaulic couplings Gasket material Deficiency: 5 year hydrostatic test of fdc piping due. Need brass caps for Siamese. Deficiency: Painted dry pendant in T2 room Deficiency: Low air supervisory on fire alarm control panel Deficiency: Control valve missing sign. 1-sign Deficiency: Dry pendant sprinkler heads throughout the buil