for Westland, MI
Travis - Westland, MI
Susan - Westland, MI
We had our annual fire extinguisher inspection today. It is always a pleasure to have this completed by Jared. He is extremely knowledgeable and efficient.
Kara - Westland, MI
Arrived on time! Was very thorough on coaching staff on how to use the alarm system in every possible scenario!
Bobby - Westland, MI
Great service thank you
Michael - Westland, MI
He was a great technician he checked everything on all our fire extinguishers very detailed on all his work while being a true professional thank you very much please send him back next year
Phillip - Westland, MI
3/12-Travis confirmed the kitchen suppression inspection/aware of alarms NWPortable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection Semiannual Kitchen System Inspection Ansul Piranha 7-7 (4)500 links (14)Nozzles Ansul R102-T9 (6)500 links (3)360 links (16)Nozzles Deficiency for Piranha 7G+7G rear hood: Rubber Hose on Piranah system has a severe kink.
3/6-Alejandra confirmed the semi-annual kitchen suppression inspection/aware of alarms NWKitchen Suppression Inspection Semiannual Kitchen System Inspection Deficiency for R-102 S-3G above hood: French Fry hood electric connections are made inside automan.
Portable Extinguishers Inspection
Kitchen Suppression Inspection
Sprinkler Survey Survey to assess loaded heads
Per fire inspector instructions, 3 additional sprinkler heads were installed in spare box. All 3 heads are pendant 155 degree standard response.
Updated Contact list with Criticom and Customer codes and user #’s also tested system for openings and closings and explained operation of alarm system. Also Replaced Zone 11 Right Front Door Battery. ***All Systems Normal and Reset ***
Portable Extinguishers Repair
Annual Fire Extinguisher Inspection (24) ABC's (1) K-Rated
Semi-Annual Kitchen Suppression System Inspection (1) Ansul 3 Gallon System
Alarm Systems Inspection
Providing faster, smarter, and more efficient fire protectionLog in