for Southgate, MI
Pat - Southgate, MI
Very knowledgeable, they helped me resolve issues that most companies would not touch. I would never recommend a different company. Service technician-John was very educated in fire suppression and safety.
Jon - Southgate, MI
Corporate maintenance director
Jon - Southgate, MI
7/19/21 confirmed with Jim for Thursday 7/22/21 Jim will put the alarms in to Test SM Kitchen Suppression and Portable Extinguishers Inspection Semiannual Kitchen System Inspection Ansul R102-S3 (2)360 links (5)Nozzles Annual Extinguisher Inspection Deficiency: Number of Extinguishers Left at Job: 2
Completed 6 Year Maintenance on 1-5 lb ABC that Required Recharge
3/26 Confirmed with Megan. GM Ashley will be on duty Monday at 8:00 AM HAVE MANAGER OPEN A CORRIGO WORK ORDER km Portable Extinguishers, Kitchen Suppression, and Emergency / Exit Lights Inspection Annual Extinguisher Inspection Semiannual Kitchen System Inspection Ansul R102-T9 (6)500 links (17)Nozzles Annual Emergency/Exit Light Inspection Deficiency: Number of Systems failed : 1 Inoperable Deficiency for Ansul R-102 9 Gallon Built In: Discharge warning device does not operate during system actuation. Deficiency: Number of Extinguishers Left at Job: 7 Inoperable Deficiency: Emergency Light by Bar Failed Recommend New Light. Inoperable Deficiency: Exit Light by Front Entrance Failed Recommend New. Inoperable Deficiency: Exit Light by Emergency Exit Failed Recommend New. Deficiency: 1- K-Class fire extinguisher due for hydro. 1- 10# - ABC Fire Extinguishers Due for Hydro Test 1-5# - ABC Fire Extinguishers Due 6 yr. maintenance 1- 5# ABC fire extinguisher due for hydro test 3-
2/25/21 confirmed WITH frank FOR 3/4/21 Pepe WILL PUT THE SYSTEM IN TO TSET. sm Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection Semiannual Kitchen System Inspection Deficiency: Number of Systems failed : 1 Deficiency: Salamander on main hood is unprotected. Deficiency: Salamander on main hood is partially outside of hood. Deficiency: Penetrations on main grill stand hood and fryer hoods need quick seals installed. Deficiency: Four holes in main hoods need to be plugged Deficiency: Main system control head does not have black box around it.
Added 1-5 lb ABC to back Stock Room. Per Fire Marshall Request
Completed Annual Fire Extinguisher inspection for 2021
Notice of Non Compliance and Repair Proposal Fire Systems of Michigan recently inspected the fire extinguishers at your establishment in accordance with applicable state statutes, local fire codes and NFPA guidelines. While inspecting your extinguishers, they were determined to be "Non-Compliant" per local fire codes. The attached proposal summarizes the non-compliance issues that were found during the inspection and the costs and actions needed to correct them. Please contact me as soon as possible to review the attached proposal and schedule the repair to your fire extinguishers. I look forward to working with you to bring your extinguishers into compliance. To discuss this proposal, please contact: Rob Harrison Phone: (616) 588-0746 Email: [email protected] EQUIPMENT REPAIR AGREEMENT This Agreement between FIRE SYSTEMS OF MICHIGAN (Company) and you (the Customer) provides for repair services only on the equipment indicated on the "Scope of Work" and "Services to Be Completed
Confirmed with Varanna for Thursday 2/18/21. SM Kitchen Suppression Inspection Semi-annual Kitchen System Inspection Ansul R102-D6 (7)500 links (17)Nozzles Deficiency: Number of Systems failed : 1 Inoperable Deficiency for Ansul R-102 6 Gallon Left of Hood: Detection line did not actuate system.
Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection Semiannual Kitchen System Inspection 2/1/21 Confirmed with mark for Wednesday @ 2:00 PM. SM 2/1/21 Left VM for Mark.. SM 2/1/21 Called and Talked to marge, she said she would have Mark call me Back. SM
12/8 Confirmed with really friendly girl who answered. km Tech arrival between 1:00 and 2:00 PM Portable Extinguishers Inspection Annual Extinguisher Inspection ( 7 ABCs )
9/24 approved by Chef Don. Tech arrival: anytime before noon. km Kitchen Suppression Inspection Semiannual Kitchen System Inspection
9/14 Confirmed with Henry for this Thursday at 8:30 AM km Portable Extinguishers and Kitchen Suppression Inspection ***COD*** - Annual Fire Extinguisher Inspections (2 FE) ***COD*** - Semi-Annual Kitchen Hood Fire Suppression System Inspection (PCL-300) Deficiency: Improper detector brackets for pyro Chem system. Deficiency: Pyro Chem control head does not have mounting bracket installed. Deficiency: Remote pull station is blocked by refrigerator.
Quarterly Sprinkler Inspection
Providing faster, smarter, and more efficient fire protectionLog in